Standard Height for Outlet Boxes The standard height for wall outlet boxes is about 12 inches from the top of the floor covering to the bottom of the receptacle box (or 16 inches to the top of the box).
Do electrical outlets have to be near the floor?
NEC 210–52 Generally, receptacle outlets in habitable rooms shall be installed so that no point along the floor line (measured horizontally) in any wall space is more than 6 feet from an outlet in that space. An outlet shall be installed in each wall space 2 feet or more in width.
What is the code for outlets on a wall?
The US National Electrical Code, Section 210.52, states that there should be an electrical outlet in every kitchen, bedroom, living room, family room, and any other room that has dedicated living space. They must be positioned at least every twelve feet measured along the floor line.
What is the standard height for light switches and outlet boxes?
For a majority of rooms, builders tend to place the bottoms of light switches 48 inches above the floor. This is a comfortable height for most home dwellers when sitting or standing, plus it makes it easier to install switches during construction.
How many feet from the floor does an outlet in a basement has to be?
A basement electrical outlet should be, at minimum, 15” from the floor. This measurement is measured from the bottom of the receptacle box.
Why do electricians install outlets upside down?
Electricians may position the outlet in an upside-down position so that you can quickly identify the switch-controlled receptacle. Since it stands out visually to most people right away – it provides convenience to the occupants to easily remember which outlet is switch controlled.
How close to a corner can an outlet be?
The National Electrical Code requires that you have an electrical outlet within 6 feet of the corner of the wall and at least 12 feet from the same wall.
How high should receptacles be in a garage?
Garage electrical outlet location: In the garage electrical outlets should be 18″ or more above floor level.
What is the maximum distance between electrical outlets?
Since the maximum distance to a receptacle is 6 feet (1.8 meters), the maximum distance between two receptacles is doubled. Therefore, the maximum distance between receptacles is 12 feet (3.6 meters).
How close to kitchen sink can outlet be?
It must be a GFCI, and it must be within 3 feet of the edge of the sink. Either behind or beside the sink is acceptable — across from the sink on an opposite wall is not. If the bathroom has two sinks, each must have an electrical receptacle within 3 feet.
Where should electrical outlets be placed?
Where To Place Electrical Outlets In New Home
- Your Kitchen. The kitchen holds many small and large electric appliances.
- The Family Room or Bar. You will need several charging locations in your family room.
- Your Living Room.
- Install Some Outdoor Outlets.
- Your Home Office.
- All Bedrooms.
How many inches from the floor can a switch be placed in new construction?
Many builders position switch boxes so the bottom of the box is 48 inches above the floor. To satisfy the accessibility requirements of the Fair Housing Act, however, the switch itself should be no more than 48 inches from the floor. To be accessible from a wheelchair, switches over cabinets should be lower.
Do finished basement receptacles need GFCI?
GFCI protection is required for 125-volt to 250-volt receptacles supplied by single-phase branch circuits rated 150 volts or less to the ground. GFCI receptacles are required in bathrooms, garages, crawl spaces, basements, laundry rooms and areas where a water source is present.
Do basement outlets require 20 amps?
Most folks will not use 20 amp outlets, but my recommendation is to always use a 20 amp circuit (#12 wire) if you can swing it. Then use 15 amp receptacles (as they’re cheaper) and receptacles are easy to switch out.
What is code for outlets in unfinished basement?
In areas of dwellings defined as unfinished basements, all 125-volt, single-phase, 15- and 20-ampere receptacles must be GFCI protected unless meeting one of the exceptions. Receptacles must be GFCI protected, even if future plans include converting the basement into a habitable room.